Meztikasa This must be located near the unit and easy to reach for the user. The battery packs must be replaced no later than every 4 years. This errichterbescheinigyng performance, material, functioning and the safe operation of the control unit. Make sure to observe the maximum possible connection options of the control unit. If components have to be checked, repaired or replaced, please contact the manufacturer.
|Published (Last):||12 November 2019|
|PDF File Size:||12.23 Mb|
|ePub File Size:||11.1 Mb|
|Price:||Free* [*Free Regsitration Required]|
To reach the operation panel, the door should be opened completely. Closing in the event of an emergency: Pc 9 9 9 4,5! Functions Opening in the event of an emergency: The red LEDs in the fire pushbutton and on the circuit board are lit.
Mortal danger to persons due to electricity! After 16 minutes the ventilation is released. Please notify your supplier immediately in case of any irregularities. Smoke and heat exhaust ventilation systems must be serviced at least once a year by a specialised SHEV company with qualified staff and in accordance with all statutory regulations building code and state building regulations.
Errichterebscheinigung control unit correspond with the actual standard of technology. To prevent electric shock, connect the earth wire first before connecting any other lines such as the mains supply line or any external lines. When using a rain sensor, make sure to observe the current consumption of 0,5 A. Danger to persons due to errichterbescheinkgung Make sure to connect shunt and terminating resistors for central smoke and heat exhaust ventilation and alarm system loops.
Stromaufnahme [A] x max. For larger cross-sections, reduce the cross-section immediately in front of the control unit. Make sure your shipment is complete prior to commencing installation. The wires are guided through the designated cable bushings from the top! The battery packs will have reached their full operating elektroinstallatoon after at least 10 hours of mains operation.
Two monitoring diodes 1N must be installed in the last conduit box in front of the drive and in accordance with the terminal connection diagram.
The battery packs must be replaced no later than every 4 years. Check if all windows open and are opened all the way before closing the windows by errichterbwscheinigung the Close button black in the fire pushbutton. Die Trennvorrichtung muss deutlich gekennzeichnet sein. This must be located near the unit and elektroinshallation to reach for the user. Zentrale mit geeignetem Befestigungsmaterial an den vorgesehenen Bohrungen 9 befestigen. These include electrical fitters or skilled fitter with training in the field of electrical equipment installation.
Never wire the components elektroinstlalation the same loop in a star configuration. H to connect the negative pole of battery pack! Dispose of the battery packs in an ecologically desirable way acc. S and battery wire! IEC — Wikipedia The inspection plate on the central unit must be renewed, and a control book must be kept.
Pay attention to earth the housing! It means the possible source of error is eliminated, but the LED lights only after 5 minutes again. The wiring type must always be authorised by the responsible authority fire service, technical inspection, fire protection etc. Crushing and cutting points! Potential crushing and cutting points between the casement and the window frame, dome lights and support frame must be secured up to a height of 2.
All works at live components may be performed only by a skilled worker with completed professional training in the field of electrical equipment installation. Use the battery pack bridge! Make sure to observe the maximum possible connection options of the control unit.
Remove and clean the detector insert. This is necessary to relate the connections correctly in case of epektroinstallation the circuit board. The isolating link has to be labeled clearly. For the wires bore the housing exclusively at the corresponding positions at back!
Use suitable mounting material. Verwenden Sie nur Original-Ersatzteile. Finish by checking all functions as well as function and operation displays on the central smoke exhaust unit and the pivoting range of the drives.
Check all devices and cable connections for external damage and dirt. The RAZ K has to errichtedbescheinigung mounted in such a way, that it is easily accessible for the maintenance staff e.
All maximum wire lengths and minimum cross sections must correspond with the technical specifications provided in these instructions. All smoke detectors actuate with smoke detector test control unit; the LED red on the detector is lit.
Netzversorgung V AC einschalten und Akkus aufstecken. TOP Related Articles.
Phänomenal Errichterbescheinigung Elektro Vorlage Sie Müssen Es Heute Versuchen